After the biomass hot blast stove is transported to the installation site, it is necessary to check whether the shape and size of the hot blast stove meet the requirements of installation space. After confirming that it can be installed, the baseline of hot blast stove body installation should be drawn on the basis of foundation. After the hot blast stove is in place on the basis, the verticality of the main body of the hot blast stove and the ground should be guaranteed. The base and the base plane should be in good contact, and the gap between them should be padded to prevent air leakage. Hot Stove Installation and Preparations for Hot Stove Installation
Preparations before installation
1. Staffing: The installation of hot blast stoves must be handled by special personnel and attended by the furnace manager, equipped with pipes, fitters, cranes, cold workers and welders.
2. Organize relevant personnel to learn materials and follow the installation process of hot blast stove according to the installation and operation instructions.
3. 设备验收热风炉运到后，应按制造厂的出厂清单，对其进行逐一清点。根据热风炉安装图纸，复核设备的完整性，检查热风炉在运输过程中是否有损坏、变形、 等情况。
3. After the equipment acceptance hot blast stove arrives, it should be counted one by one according to the list of manufacturer. According to the installation drawings of hot blast stove, check the integrity of equipment, check whether the hot blast stove is damaged, deformed, etc. in the course of transportation.
4. 确定安装地点 安装地点最好能接近供热地点，以缩短送水管路，降低基建费用，减少管路的散热损失。同时，要考虑补给水和排水方便，燃料和灰渣的存放 与运输方便。
4. It is better to locate the installation site close to the heating site in order to shorten the water supply pipeline, reduce the cost of infrastructure and reduce the heat loss of the pipeline. At the same time, we should consider the convenience of water supply and drainage, and the convenience of storage and transportation of fuel and ash.
5. Hot-blast stove house layout should conform to the "Industrial Hot-blast Stove House Design Code".
6. 地基施工，热风炉应放在水泥基础上，基础厚度要根据实际土层承载 能力由使用单位确定。
6. In foundation construction, the hot blast stove should be based on cement, and the thickness of the foundation should be determined by the user according to the actual bearing capacity of the soil layer.
7. When unloading the biomass hot-blast stove, pay attention to using steel wire rope to hoist it without damaging any part of the large parts of the hot-blast stove.
8. 生物质热风炉如需起吊，其起重设备能力应按照热风炉的实际重量和现场 情况决定，起吊位置应符合规定，切勿任意在其它位置上起吊。
8. If a biomass hot blast stove needs to be hoisted, its hoisting equipment capacity should be determined according to the actual weight of the hot blast stove and the site conditions. The hoisting position should be in accordance with the regulations and should not be hoisted at any other position. 三、尾部烟道的安装
III. Installation of tail flue
After the installation of biomass hot blast stove, the flue, etc. are assembled according to the regulations. When the flue is installed, asbestos rope is padded between the flanges, and the vertical degree of the connecting flue pipe is checked by hanging line method. If there is deviation, the hollow position of the connecting bolt of the flange can be adjusted.
IV. Installation of Electronic Control Cabinet
The electric control cabinet is equipped with induced draft fan, blower, circulating water pump, etc.
Cautions for Hot Stove Installation
1. It is strictly forbidden to install an atmospheric hot stove as a pressurized hot stove. It is strictly forbidden to use hot blast stoves with incomplete safety accessories such as water level gauge, safety valve and pressure gauge.
2. Endoscopy should be used to check whether the welding connection of biomass hot stove is consistent with the drawing design.
3. Inspection hot stove after installation. Hot stoves are inspected regularly every year. Hot stoves that have not been inspected regularly and safely shall not be used. Safety accessory safety valve of hot stove is inspected regularly every year, pressure gauge is inspected every half year. Safety accessory that has not been inspected regularly shall not be used.
4. After passing the inspection, the hot blast stove is tested.
标签:  翅片管 热风炉 常州铝艺大门 常州铝艺护栏 铝艺大门 铝艺大门厂家